This example in connection with our previous post,

**How to calculate Aeration Tank Volume? **

Total BOD to be removed (Influent) = 250 mg/l (assume) x 1400 = 350 kg/Day (we consider 1400 M3/Day Effluent Plant)

Hence O_{2 }to be transferred =350 kg/Day

Method of Aeration = Fine Bubble Diffuser

SOTE (

Standard OFor 300 mm disc type diffuser submergence) =20%_{2}Transfer Efficiency

Hence O_{2} required 350/0.20 =1750 kg/day.

Assuming *alpha* Factor (Ratio of SOTE in clean water to effluent water)=0.8 and

Another *alpha* Factor (Factor for fouling of diffusers) =0.8

Oxygen requirement =2734 kg/day {Oxygen % in the atmospheric air = 23.2%}

Hence, Air Requirement =11790 kg/day {With Sp.gravity of Air at 50°C =0.8 kg/M³}

**Air requirement = 14737 M³/Day = 614 M³/Hr**

Allowing 5% extra, **So 650 M³/Hr @ 0.5 kg/cm2 blower can be select **

further note below points too.,

one more point to be consider

the Depth of aeration Tank, suppose it is 4 metre depth select 0.5 or 0.6 kg/cm² in blower side.

Thank Sir.

Excellent . Informative,

The info is very useful . For my clarification, in Air requirement of aeration tank topic

Total BOD to be removed = 250 (assume) x 1400 = 350 kg/Day; What does 1400 denotes?

And for more details to know can you provide me the contact mail id. since I work in STP concern I like to know more about Calculation and process details from your website.

Thank you,

1400 m3/day effluent to be treated

What is 1400 in this calculation

effluent load 1400 m3/day taken to account.

Can you Please explain these calculations in detail

now, check it again the post has been updated, thanks to drop the commands

khud hi samajh le na be. kyun dass raha hai yar dassan kha le lassan

Total BOD to be removed = 250 (assume) x 1400 = 350 kg/Day

what is 1400?

thanks your point out – 1400 we consider as effluent qty in m3/day

Nice Post!! Really helpful.

Can you tell me roughly SOTE % for a tubular fine bubble (say 600 mm to 1000mm) & Disc Type Coarse Bubble(80mm, 150mm)?

Is there any thumb rule for calculating it?

waiting for your reply

How to find out this value? – explain

Oxygen requirement =2734 kg/day

Hence, Air Requirement =11790 kg/day

2734 kg/day /23.2% (Oxygen % in the atmospheric air = 23.2%) = 11784 kg/day air

Plant capacity

1400 assuming plant capacity

yes, this is plant capacity in example case we taken into account.

Nice information sir.thanks

Nice information sir.thanks but finally what is volume of aeration tanks??

Sir what is 250 in this calculation

250 is mg/l of effluent BOD (assume)

Pls sir explain this calculation in detail

how to calculate 350mg/d o2

Hi Sir,

Thank you for your valuable knowlege.

You have mention that Sp.gravity of Air at 50°C =0.8 kg/M³ , but this value is about 1.05 kg/M³

This will change the Air requirements,

Regards,

Dnyaneshwar

If aeration tank death is 5 metre then what capacity blower require and why?

Does the submergence SOTE vary with the depth ?

i have mechanical areator , make gsd ar 511 model what its oxygen transfer rate

How come oxygen required-2734 kg/d,

How much O2 required for Per kg of BOD.

Plz elaborate.

O2 required 350/0.20 =1750 kg/day.and use Two alpha factor efficiency i.e %sote and fouling of diffuser [(1750/80%)/80%].

KG of O2 required for carbonaceous BOD removal can range from 0.7 Kg/Kg BOD for high rate activated sludge with short detention of Biomass (low sludge age) up to 1.5 kg/kg BOD for extended aeration with long detention of Biomass (MLSS, i.e., (long sludge age) in the bio system,

we account 1kg/kg of BOD.

Hope, you will clear.

Sir useful information but what is mean by sote for submergence of diffuser and what is mean by fouling of diffuser

Submergence mean depends on depth of aeration tank the the sote will vary more depth more percentage of oxygen transfer but increase air blower power,similarly fouling mean it affects air discharge due to excess of MLSS and other colloids in aeration tank.

What is the basis of the assumption of 0.8 for both alpha1 and alpha2.?

How can I determine it for other cases?

What will be the % oxygen transfer efficienty for 1000 mm long x 67 mm OD fine bubble tubular air diffuser silicone basaed membrane

Dear Sir,

How to calculate BOD and Air quantity in Aeration Tank

Dear sir,

if it is using jet aerators (30 hp) and blower(5 hp) then find the air producing rate per hour

You can see the manufacturer catalog, model to model it will vary and depends on Depth of installation,the output air CFM vary, plz ask the supplier, normally @ 0.5 kg/cm2 pressure you can install that jet aerator upto 4 meter depth?

Dear Sir,

Can u tell me how to calculate quantity of mbbr media required in stp/etp.

Mr.Shivanandan, what should be the optimum depth of aeration tank to get maximum SOTE ?

Regards

suggested depth 4 to 5 meter, but SOTE ! influence many factor depth, bubble size, temperature of the medium, bubble travel either it travels direct upward from the bottom of diffuser or certain inclination / angels.

Dear Sivanandan,

Can u tell me how to calculate quantity of mbbr media required in stp/etp.

sir my air requirement is 650cum/h my aeration tank depth is 4mt how to calculate blower capacity

exactly my same question

What will be efficiency need to take during actual purchase?

how can we select blower pressure?

here directly it is given to select 0.5kg/cm2.

on which factor we can select?

Please provided details calculation xygen requirement =2734 kg/day {Oxygen % in the atmospheric air = 23.2%}

Hence, Air Requirement =11790 kg/day {With Sp.gravity of Air at 50°C =0.8 kg/M³}

Air requirement = 14737 M³/Day = 614 M³/Hr

Thanks sir ! Very useful information.

Sir please provide detail calculation for pipeline distribution and diffuser requirements for the above capacity

thanks but I need how select the blower suitable ?

Very useful Easy and detailed design calculation.thank you sir

you are welcome

Our aeration tank capacity is 95 cu.m x 3nos=285cu.m.Sir how can I find matching aeration pump capacity for this plant? Recently we have 3.7kw x 3nos submersible pumps.

Thanks. What is the basis for calculating require aeration tank size, and diffuser qty

Thank you

How did you get 2734 kg/cm2

Sir, for alpha factor, it is for clean water right? may i know how to calculate alpha factor?

Then for the O2 required in the calculation is the total oxygen supply by the blower to all diffuser in the aeration tank right?

O2 requirement = 2734 kg / day how??