Normally, the filter backwash water sludge very tough to remove or separate that one, generally in many plants that will have design the back wash water pipe line laid into main effluent collection tank. But this is not a right method.
Instead of that, try this method, though which has bit of cost investment involve, this is only an perfect [....]
Servyeco Group of Spain has newly developed Natural plant based Coagulants for waste water treatment, they took several test successfully using with different category plant’s waste water, they extracts the liquids from Acacia plant.
Is a natural cationic coagulant that is extracted from the bark of Acacia Negra (Acacia mearnsii) the product belongs to the family of the tannins [....]
Coagulation is an primary process of any kind of water treatment plant, that process must be performed using with cost effective and commonly used coagulants.
General and 7 most commonly used coagulants in water treatment plant is under:
1.Alum (aluminum sulfate), Al2(SO4)3. Still, the most common coagulant in the United States, it is often [....]
Principle and Design of Spray Aerators: The system consist more spray nozzles, which are connected in a pipe, similarly many set of pipes are well connected like square, circle and rectangle shaped form and those bunch of pipes finally links to common pipe manifold, that pipe grid located over an open-top tank
The water leaves each nozzle in a fine [....]
Many guys are asking frequently, what are the Technologies / treatment process are available to Drinking as well as Effluent Water Parameter? numerous methods that are available to control or removal the impurities presents in the water.
Generally in textile effluent Color removal is very difficult Task. similarly in the same plant, the feed water of Reverse Osmosis plant turbidity [....]
How to Handle Vacuum Crystallizer / Cooling Crystallizer, those are commission this plant, the following subjects to be checked, while operating the plant
After commission the Vacuum Crystallizer before going to start the system, Ensure the Steps / Checklist
1. Raise the vacuum first using by cooling tower after reaching around 100- 200 mmHg. Inject the steam into Primary Condenser [....]