In water treatment plant, we need to be evaporated water or Reactivated sludge (MLSS) and Chemical sludge.In this case we should know the Heat energy calculation for Sludge drying.
It is help to analyze quondam of Heat Energy require to evaporate such a medium.
Ok, for example. we’ll take. A Sludge containing 80% water is to be dried at 100°C [....]
River and Stream Flow (Discharge) measurement is very important to provide the basic data required for river or stream water quality. The total discharge for a stream can be estimated by float method with wind
and other surface effects, by die study, or by actual subsection flow measurement, depending on cost,
time, man-power, local conditions and so on. The discharge [....]
The packed bed of adsorbent can be regenerated. If the organic material is volatile, the carbon bed may be regenerated by steaming. However, it is more conven-tional to remove the carbon and reprocess the material through a furnace.In large installations, the furnace is installed as part of the carbon installation; in smaller installations, the carbon may be discarded, or removed [....]
This example in connection with our previous post,
How to calculate Aeration Tank Volume?
Total BOD to be removed (Influent) = 250 mg/l (assume) x 1400 = 350 kg/Day (we consider 1400 M3/Day Effluent Plant)
Hence O2 to be transferred =350 kg/Day
Method of Aeration = Fine Bubble Diffuser
SOTE (Standard O2 Transfer Efficiency For 300
Relationship between TS,TSS and TDS
These three solids tests can be related with Equation :TS = TSS +TDS
Total Solids. For regulatory and treatment purposes, total solids (TS) can first be classified as
suspended or dissolved. Total solids, as defined by Standard Methods and EPA, is the material
residue left in a vessel after evaporation of a sample and [....]