How to Handle Vacuum Crystallizer / Cooling Crystallizer, those are commission this plant, the following subjects to be checked, while operating the plant
After commission the Vacuum Crystallizer before going to start the system, Ensure the Steps / Checklist
1. Raise the vacuum first using by cooling tower after reaching around 100- 200 mmHg. Inject the steam into Primary Condenser [....]
Water Hammer or surge, It is big headache to every Industry,Why and How it is happen? before that we should know What is this?
Any Liquid media /Water, which is passing into the pipe, all of sudden the flow restricts /Shut off of it by the valve across the flow, the back pressure will created due to return the media, [....]
The DOW Membrane recently estimated the various solutes rejection ratio in their own production of membrane of FT30 Model
I think, probably most of the membrane’s rejection ratio has to be similar one and note that, solutes Molecular weight also they given, further they indicated clearly this is quick screen, particularly with changes in feed water concentration, pH and temperature [....]
If you have Biological tank of your Water Treatment stream, Install Online Dissolved Meter to the tank and Connect suitable Frequency Driver / Inverter for your Air Blower System.
Definitely, which will help to monitor and control the Excess Oxygen Develops. Similarly it will adjust automatically when oxygen will sort fall below the set limit into the Biological Tank,
Are you going to construct new ETP for your existing industry or new industry, ensure this checklist, the following factors must be adhered while design the Efflent Treatment Plant
The Most Important Factors of ETP Design | Selection are
1. What national or international standards must you comply with?
2. What is your waste? What volume of effluent do you [....]
How much % of recovery is possible in textile Reverse Osmosis Plant?, Any environmental engineer try to get maximum Recovery from the RO plant, generally it is not easy in textile plant, As of my knowledge the following parameter / factors gives more threaten to us,
Usually, In First Stage of RO plant 65-70 %; second stage 50-55%; Third Stage [....]